TITAN Products announce the release of a new Modbus to BACnet Gateway operating to ANSI/ASHRAE Standard 135.
Do you need to convert Modbus into BACnet for your BMS? The CCI-2X485 is designed to interface third party Modbus control products on to a BACnet system.
Monitor your Buildings
The BACnet gateways set up the Modbus to BACnet mapping objects through the use of a PC with software provided by TITAN Products and the FPT-601 Field Programming Tool. .
In order to upload the mapping from a PC to the CCI gateway a Titan FPT-601 Field Programming Tool. is required. The PC software is supplied with the FPT601.
The Titan BACnet gateway operates as a Modbus RTU-Master and can support the following Modbus mapping in any combination:
200 (150 with Intrinsic Reporting) Modbus Discrete Inputs to BACnet Binary Input Objects or
200 (150 with Intrinsic Reporting) Modbus Coils to BACnet Binary Value Objects or
200 (150 with Intrinsic Reporting) Modbus Input Registers to BACnet Analog Input Objects or
200 (150 with Intrinsic Reporting) Modbus Holding Registers to BACnet Binary Value Objects or
200 (150 with Intrinsic Reporting) Modbus Holding Registers to BACnet Analog Value Objects
Operating on native BACnet over MS/TP TITAN Products offer bespoke software engineering for customers who have a need to create a special control function or interface their products onto a BACnet system. This customised control allows for greater control over energy management and the potential of larger energy savings to be made.
The CCI-2X485 is available with 24VAC/DC, 115VAC or 230VAC supply options.